# SEER: Wikis

Note: Many of our articles have direct quotes from sources you can cite, within the Wikipedia article! This article doesn't yet, but we're working on it! See more info or our list of citable articles.

# Encyclopedia

(Redirected to Seasonal energy efficiency ratio article)

The efficiency of air conditioners is often rated by the Seasonal Energy Efficiency Ratio (SEER) which is defined by the Air Conditioning, Heating, and Refrigeration Institute in its standard ARI 210=240, Performance Rating of Unitary Air-Conditioning and Air-Source Heat Pump Equipment. [2] The SEER rating of a unit is the cooling output in Btu(British thermal unit) during a typical cooling-season divided by the total electric energy input in watt-hours during the same period. The higher the unit's SEER rating the more energy efficient it is.

For example, consider a 5000 BTU/h air-conditioning unit, with a SEER of 10, operating for a total of 1000 hours during an annual cooling season (e.g., 8 hours per day for 125 days).

The annual total cooling output would be:

5000 BTU/h * 8 h/day * 125 days = 5,000,000 BTU

With a SEER of 10, the annual electrical energy usage would be about:

5,000,000 BTU / 10 BTU/W·h = 500,000 W·h

The average power usage may also be calculated more simply by:

Average power = (BTU/h) / (SEER, BTU/W·h) = 5000 / 10 = 500 W

0.5 kW * 20¢/kW·h = 10¢/h

## Relationship of SEER to EER and COP

SEER is related to the Energy Efficiency Ratio (EER), which is the ratio of output cooling in Btu/Hr and the input power in watts W at a given operating point and also to the coefficient of performance (COP) commonly used in thermodynamics. Performance ratios can be a unitless output over input ratio, never to exceed one, and it is also proper to state what kind of energy is in the numerator and denominator. The COP of a heat pump is determined by dividing the power output of the heat pump by the electrical power needed to run the heat pump, with both powers measured using the same units, e.g. watts. The higher the COP, the more efficient the heat pump. For example resistive heat has a COP = 1. The EER is the efficiency rating for the equipment at a particular pair of external and internal temperatures. EER (Btu/(W*hr)) is converted to COP (Btu/Btu (Note: some may write W/W)) by dividing by 3.413 Btu/(Hr*W).

The SEER is calculated at a part loaded standardized ARI test. (Defined on/off cycle) This more closely represents the performance from equipment cycling, instead of the steady state conditions under which the EER is measured.

Typical EER for residential central cooling units = 0.875 X SEER
SEER is always a higher value than EER for the same equipment.

http://ari.org/ARI/util/showdoc.aspx?doc=1028 ARI STANDARD 210/240-2008

A SEER of 13 is approximately equivalent to a COP of 3.43, which means that 3.43 units of heat energy are removed from indoors per unit of work energy used to run the heat pump.

## Theoretical maximum

The SEER and EER of an air conditioner are limited by the laws of thermodynamics. The refrigeration process with the maximum possible efficiency is the Carnot cycle. The COP of an air conditioner using the Carnot cycle is:

$COP_{Carnot}=\frac{T_{C}}{T_{H}-T_{C}}$

where TC is the indoor temperature and TH is the outdoor temperature. Both temperatures must be measured using a thermodynamic temperature scale such as Kelvin or Rankine. The EER is calculated by multiplying the COP by 3.413 which is the conversion factor from BTU/h to Watts:

$EER_{Carnot}=3.413 \frac{T_{C}}{T_{H}-T_{C}}$

For an indoor temperature of 80F (299.81 K) and an outdoor temperature of 95F (308.15 K), the above equation gives an COP of 36.0, or an EER of 123. This is about 10 times as efficient as a typical home air conditioner available today.

The maximum EER decreases as the difference between the inside and outside air temperature increases, and vice versa. In desert climates, where the temperature may be as high as 120F, the maximum COP drops to 13.5, or an EER of 46 (assuming an outdoor temperature of 120F and an indoor temperature of 80F).

The maximum SEER can be calculated by averaging the maximum EER over the range of expected temperatures for the season.

## US government SEER standards

SEER rating more accurately reflects overall system efficiency on a seasonal basis and EER reflects the system’s energy efficiency at peak day operations. Both ratings are important when choosing products. As of January 2006, all residential air conditioners sold in the United States must have a SEER of at least 13. ENERGY STAR qualified Central Air Conditioners must have a SEER of at least 14.

Today, it is rare to see systems rated below SEER 9 in the United States because aging, existing units are being replaced with new, higher efficiency units. The United States now requires that residential systems manufactured after 2005 have a minimum SEER rating of 13, although window units are exempt from this law so their SEERs are still around 10.

Substantial energy savings can be obtained from more efficient systems. For example by upgrading from SEER 9 to SEER 13, the power consumption is reduced by 30% (equal to 1 - 9/13). It is claimed that this can result in an energy savings valued at up to US$300 per year depending on the usage rate and the cost of electricity. With existing units that are still functional and well-maintained, when the time value of money is considered, retaining existing units rather than proactively replacing them may be the most cost effective. However, the efficiency of air conditioners can degrade significantly over time.[1] Therefore, maintenance should be performed regularly to keep their efficiencies as high as possible. But when either replacing equipment, or specifying new installations, a variety of SEERs are available. For most applications, the minimum or near-minimum SEER units are most cost effective, but the longer the cooling seasons, the higher the electricity costs, and the longer the purchasers will own the systems, incrementally higher SEER units are justified. Residential split-system ACs of SEER 20 or more are now available, but at substantial cost premiums over the standard SEER 13 units. ## Calculating the annual cost of power for an air conditioner Air conditioner sizes are often given as "tons" of cooling where 1 ton of cooling is being equivalent to 12,000 BTU/h. This is approximately the power required to melt one ton of ice in 24 hours. The annual cost of electric power consumed by a 72,000 BTU/h (6 ton) air conditioning unit operating for 1000 hours per year with a SEER rating of 10 and a power cost of 12¢ per kilowatt-hour (kW·h) may be calculated as follows: unit size, BTU/h × hours per year, h × energy cost,$/kW·h ÷ SEER, BTU/W·h ÷ 1000 W/kW

Example:

(72,000 BTU/h) × (1000 h) × (12¢/kW·h) ÷ (10 BTU/W·h) ÷ (1000 W/kW) = $864 annual cost As another example, a theoretical residential structure near Chicago with a calculated cooling load of 4 tons: (4 tons) × (12,000 BTU/h/ton) = 48,000 BTU/h. The estimated cost of electrical power for the 4 ton unit with a SEER rating of 10 and an energy cost of 10¢ per kilowatt-hour, using 120 days of 8 hours/day operation, would be: (48,000 Btu/h) × (960 h/year) × (10¢/kW·h) ÷ (10 BTU/W·h) ÷ (1000 W/kW) =$461 annual cost

## References

1. ^ US Department of Energy Framework Public Meeting for Residential Central Air Conditioners and Heat Pumps (June 12, 2008) at 35-36 (transcript) [1].

The efficiency of air conditioners is often rated by the Seasonal Energy Efficiency Ratio (SEER) which is defined by the Air Conditioning, Heating and Refrigeration Institute in its standard ARI 210/240, Performance Rating of Unitary Air-Conditioning and Air-Source Heat Pump Equipment.[1]

The SEER rating of a unit is the cooling output in Btu (British thermal unit) during a typical cooling-season divided by the total electric energy input in watt-hours during the same period. The higher the unit's SEER rating the more energy efficient it is.

For example, consider a 5000 BTU/h air-conditioning unit, with a SEER of 10 BTU/W·h, operating for a total of 1000 hours during an annual cooling season (e.g., 8 hours per day for 125 days).

The annual total cooling output would be:

5000 BTU/h × 8 h/day × 125 days/year = 5,000,000 BTU/year

With a SEER of 10, the annual electrical energy usage would be about:

5,000,000 BTU/year / 10 BTU/W·h = 500,000 W·h/year

The average power usage may also be calculated more simply by:

Average power = (BTU/h) / (SEER) = 5000 / 10 = 500 W

If your electricity cost is 20¢/kW·h, then your cost per operating hour is:

0.5 kW * 20¢/kW·h = 10¢/h

## Relationship of SEER to EER and COP

The Energy Efficiency Ratio (EER) of a particular cooling device is the ratio of output cooling (in Btu/hr) to input electrical power (in Watts) at a given operating point (indoor and outdoor temperature and humidity conditions). The Seasonal Energy Efficiency Ratio (SEER) has the same units of Btu/W·hr, but instead of being evaluated at a single operating condition, it represents the expected overall performance for a typical year's weather in a given location. The EER is related to the coefficient of performance (COP) commonly used in thermodynamics, with the primary difference being that the COP of a cooling device is unit-less: the cooling load and the electrical power needed to run the device are both measured using the same units, e.g. watts. Therefore a COP is universal and can be used in any system of units. However, the COP is an instantaneous measure (i.e. a measure of power divided by power), whereas both EER and SEER are averaged over a duration of time (i.e. they are measures of energy divided by energy). The time duration considered is several hours of constant conditions for EER, and a full year of typical meteorological and indoor conditions for SEER.

The SEER is calculated at a part loaded standardized ARI test. (Defined on/off cycle) This more closely represents the performance from equipment cycling, instead of the steady state conditions under which the EER is measured.

Typical EER for residential central cooling units = 0.875 × SEER. SEER is generally a higher value than EER for the same equipment.[1]

A SEER of 13 is approximately equivalent to a COP of 3.43, which means that 3.43 units of heat energy are removed from indoors per unit of work energy used to run the heat pump.

## Theoretical maximum

The SEER and EER of an air conditioner are limited by the laws of thermodynamics. The refrigeration process with the maximum possible efficiency is the Carnot cycle. The COP of an air conditioner using the Carnot cycle is:

$COP_\left\{Carnot\right\}=\frac\left\{T_\left\{C\right\}\right\}\left\{T_\left\{H\right\}-T_\left\{C\right\}\right\}$

where $T_C$ is the indoor temperature and $T_H$ is the outdoor temperature. Both temperatures must be measured using a thermodynamic temperature scale based at absolute zero such as Kelvin or Rankine. The EER is calculated by multiplying the COP by 3.413 which is the conversion factor from BTU/h to Watts:

$EER_\left\{Carnot\right\}=3.413 \frac\left\{T_\left\{C\right\}\right\}\left\{T_\left\{H\right\}-T_\left\{C\right\}\right\}$

For an indoor temperature of 80°F (299.81 K) and an outdoor temperature of 95°F (308.15 K), the above equation gives a COP of 36.0, or an EER of 123. This is about 10 times as efficient as a typical home air conditioner available today.

The maximum EER decreases as the difference between the inside and outside air temperature increases, and vice versa. In desert climates, where the temperature may be as high as 120°F, the maximum COP drops to 13.5, or an EER of 46 (assuming an outdoor temperature of 120°F and an indoor temperature of 80°F).

The maximum SEER can be calculated by averaging the maximum EER over the range of expected temperatures for the season.

## US government SEER standards

SEER rating more accurately reflects overall system efficiency on a seasonal basis and EER reflects the system’s energy efficiency at peak day operations. Both ratings are important when choosing products. As of January 2006, all residential air conditioners sold in the United States must have a SEER of at least 13. ENERGY STAR qualified Central Air Conditioners must have a SEER of at least 14.

Today, it is rare to see systems rated below SEER 9 in the United States because aging, existing units are being replaced with new, higher efficiency units. The United States now requires that residential systems manufactured after 2005 have a minimum SEER rating of 13, although window units are exempt from this law so their SEERs are still around 10.

Substantial energy savings can be obtained from more efficient systems. For example by upgrading from SEER 9 to SEER 13, the power consumption is reduced by 30% (equal to 1 − 9/13). It is claimed that this can result in an energy savings valued at up to US$300 per year depending on the usage rate and the cost of electricity. With existing units that are still functional and well-maintained, when the time value of money is considered, retaining existing units rather than proactively replacing them may be the most cost effective. However, the efficiency of air conditioners can degrade significantly over time.[2] Therefore, maintenance should be performed regularly to keep their efficiencies as high as possible. But when either replacing equipment, or specifying new installations, a variety of SEERs are available. For most applications, the minimum or near-minimum SEER units are most cost effective, but the longer the cooling seasons, the higher the electricity costs, and the longer the purchasers will own the systems, incrementally higher SEER units are justified. Residential split-system ACs of SEER 20 or more are now available, but at substantial cost premiums over the standard SEER 13 units. ## Calculating the annual cost of power for an air conditioner Air conditioner sizes are often given as "tons" of cooling where 1 ton of cooling is being equivalent to 12,000 BTU/h. This is approximately the power required to melt one ton of ice in 24 hours. The annual cost of electric power consumed by a 72,000 BTU/h (6 ton) air conditioning unit operating for 1000 hours per year with a SEER rating of 10 and a power cost of 12¢ per kilowatt-hour (kW·h) may be calculated as follows: unit size, BTU/h × hours per year, h × energy cost,$/kW·h ÷ SEER, BTU/W·h ÷ 1000 W/kW

Example:

(72,000 BTU/h) × (1000 h) × ($0.12/kW·h) ÷ (10 BTU/W·h) ÷ (1000 W/kW) =$864 annual cost

As another example, a theoretical residential structure near Chicago with a calculated cooling load of 4 tons:

(4 tons) × (12,000 BTU/h/ton) = 48,000 BTU/h.

The estimated cost of electrical power for the 4 ton unit with a SEER rating of 10 and an energy cost of 10¢ per kilowatt-hour, using 120 days of 8 hours/day operation, would be:

(48,000 Btu/h) × (960 h/year) × ($0.10/kW·h) ÷ (10 BTU/W·h) ÷ (1000 W/kW) =$461 annual cost

## Maximum SEER Ratings

Today there are residential AC units available with SEER ratings up to 26. [3] There are a variety of technologies that will allow SEER and EER ratings to increase further in the near future.[4] Some of these technologies include rotary compressors, inverters, DC brushless motors, variable-speed drives and integrated systems.[4]

## References

1. ^ a b
2. ^ US Department of Energy Framework Public Meeting for Residential Central Air Conditioners and Heat Pumps (June 12, 2008) at 35– 36 (transcript) [1].
3. ^
4. ^ a b

Seer or Seers or SEER may refer to:

Predicting the future
Religion
Places
• Seer Gharbi, a Union Council in NWFP, Pakistan
• Seer Green, a village and civil parish in Buckinghamshire, England
People
Other